Home and Away modes provide the utmost in leak detection throughout continued normal water use without interrupting service. The default programming is as follows: Home mode 30 minutes uninterrupted flow allowance; Away mode 30 second flow allowance. Anytime normal, episodic flow stops, the flow allowance timer is always reset. The default flow sensitivity (Drip Rate) is 2 ounces-per-minute. Drip Rate and Home/Away mode settings are fully adjustable. From the local keypad, to place the System in the Away mode, press the Away button. To return to the Home mode, press the Home button. These functions can be automated through security system interfaces. See page 16 of the instructions for more information. Mode changes can also be done easily through the app on Wi-Fi-connected systems.